A standby generator is designed to provide a secondary source of power for a building or facility. Also known as an emergency generator or back up generator.
In the event of mains failure to a building the standby generator is remotely started and then switched over to feed the building loads until mains is restored.
In a fully automated system, this function is performed by an ATS (auto transfer switch). The ATS can be a separate panel or integrated into the building switchgear controls or generator controller.
In the majority of cases, the starting and transfer of the generator power is automatic, but sometimes it is done manually using a manual changeover switch.
How do I know my generator will start?
When the generator is not in use and waiting to be called into action, it is vital that the system is healthy with no alarms, the breakers are all closed and the starting battery is kept on charge.
Sometimes the smallest failure can prevent your generator from starting, such as failing to keep your fuel tank topped up! It is important to keep up to date with your fuel services.
It is also common to have an engine block heater connected to your standby generator that keeps your engine warm and prevents cold starting. Diesel engines can fail to start when they are cold, so this is an important consideration.
How often should I service my standby generator?
A standby generator is different to a prime or continuous loaded generator, as it is only called to run on load in an emergency situation. Sometimes standby generators are not run in an emergency situation for years…or even at all if the mains power is secure!
This means that it is imperative to perform routine checks and servicing to ensure that it remains 100% functional. We recommend at least 2 service visits per year for your standby generator to keep it in a fully functional state. At Solent Power we offer a generator service and maintenance to keep your generator running smoothly.
It is also recommended to perform mains fail tests, or black building tests at least annually to prove the control systems and that the standby generator can handle the building load.
If a building load test is not operationally possible, you can use a loadbank to prove the load acceptance of your generator. A loadbank is a ‘dummy load’ that connects to your generator to simulate your building being connected.
If you require help or support with your standby generator and need expert advice, please contact us at Solent Power and discuss your requirements and we will be happy to advise and accommodate.
Paul is the MD of Solent Power and specialises in emergency power solutions, helping to protect your facilities from power loss. Get in touch with us today to discuss the different power brands that we can offer and how they can suit your needs.
Solent Power Ltd (Company Number 12622565) is a company registered in England and Wales. Our registered office is located at Unit 7 Mayflower Close, Chandler’s Ford Industrial Estate, Eastleigh, Hampshire, SO53 4AR. VAT No. 363504018
To provide the best experiences, we use technologies like cookies to store and/or access device information. Consenting to these technologies will allow us to process data such as browsing behaviour or unique IDs on this site. Not consenting or withdrawing consent, may adversely affect certain features and functions.
The technical storage or access is strictly necessary for the legitimate purpose of enabling the use of a specific service explicitly requested by the subscriber or user, or for the sole purpose of carrying out the transmission of a communication over an electronic communications network.
The technical storage or access is necessary for the legitimate purpose of storing preferences that are not requested by the subscriber or user.
The technical storage or access that is used exclusively for statistical purposes.The technical storage or access that is used exclusively for anonymous statistical purposes. Without a subpoena, voluntary compliance on the part of your Internet Service Provider, or additional records from a third party, information stored or retrieved for this purpose alone cannot usually be used to identify you.
The technical storage or access is required to create user profiles to send advertising, or to track the user on a website or across several websites for similar marketing purposes.